- Air Conditioning
An understanding Worldwide
The Multi-Zone Control Panel operates the network of leak detection zones. A zone can be a single point or many metres long and the whole network is continuously monitored for leaks and continuity.
Zones are electrically isolated from each other and individually displayed so the system can accept and report any number of simultaneous or consecutive zone alarms - true multiple leak reporting - an alarm zone has no effect on the normal monitoring of its neighbours or the rest of the system.
LEDs provide clear and easy to understand status and alarm information. Output relays are provided for connection to remote alarms, BMC etc. Leak detection is shown clearly as LEAK. Sensor or cable damage or failure is shown as SYSTEM FAULT.
Sizes: 4,8,16,32,64 and 96 Zones
Water/liquid detection (other 12VDC latchable sensing devices can also be connected)
110/230 VAC, 50Mhz, mains operated, 12VDC internal and battery back-up
Light grey powder coated steel enclosure
H292mm x W285mm x D90mm (4, 8 and 16 zone - see relevant data sheet)
Wall/Surface mounted (special mounting arrangements to order)
LEAK - continuous water/liquid detection - each zone separately SYSTEM FAULT - sensor or leader cable damage, failure or disconnection
Flashing LEDs for LEAK or SYSTEM FAULT (all alarms displayed separately and continuously, until corrected and restored)
Mains power supply
internal 12VDC supply
alarm accept (mute)
Mute (buzzer silence/alarm accept) button
1. LEAK in any zone - DPCO relay
2. SYSTEM FAULT in any zone - SPCO relay
3. Drop dead/power fail - SPCO relay
4. LEAK in each individual zone - SPCO relay - optional
All relays have "clean" volt-free contacts
16-Zone Control Panel