HVAC Europe closing
From Thursday 23rd of January 2020 12:00 hrs until Friday 24th of January 2020 HVAC Europe will be closed. More...
Floodline Ranger has been designed for use as a stand alone system or in conjunction with other Floodline Control Panels for continuous Leak Detection.
Floodline Ranger is designed to be snapped onto standard 35mm DIN rail. The unit is supplied in its own housing but can be easily mounted in existing electric or instrumental cbinets with spare rail space.
Up to 1500M (5000ft) of sensor cable can be monitored by Ranger. Ranger's typical applications include plant rooms, warehouses, libraries and museums.
Once a leak is detected, the device can trigger an audio/visual alarm as well as triggering onward communication to BMS or similar. The LED indicator on the device shows the distance to the leak.
The sensing cable detects the presence of water at any point along its length. The cable is available in different, pre-terminated lengths with locking connectors to facilitate joining lengths together. The conductive-polymer technology and fluoro polymer construction make our sensing cable mechanically strong and resistant to corrosion and abrasion.
Storage Temperature: -40°C ~ 60°C
Operating Temperature: -20°C ~ 50°C
Operating Humidity: 5% ~ 95% (No condensation)
Power Supply: 12VDC, 3W
Serial Interface; Network configuration: RS485 communication mode. BAUD rate can be selected, optional address for 0 to 247. Default BAUD rate is 9600 and address is 0. MODBUS RTU
Relay contacts: 125VAC 0.5A, 24VDC 1A normally open (can be normally closed)
Construction: ABS plastic housing
Mounting: 35mm DIN RAIL
Connections: Screw terminals for all wiring
Indicators: LEDs for POWER, Cable Fault, LEAK, COMMS
Cable maximum length: 1500M
Accuracy: 0.5% ± 0.5m
Construction: conductive-polymer with fluoropolymer construction
Diameter: 6.00mm (nominal)
Colour: High-visibility yellow
Maximum continuous operating temperature: 70°C
Drying Time: Cable dries and resets within 15 minutes after removal from standing water.
Standard Cleaning Method: Wipe with clean, damp cloth
This brochure contains the following information
Long line detection cable